CircuitSolver Union Assembly with Strainer (CSUAS)
CircuitSolver® thermostatic balancing valves automatically balance a domestic hot water system (DHWS) in a fraction of the time required by traditional manual balancing methods.
The CircuitSolver® Union Assembly with Strainer features a union with an optional check valve built into the body of the CircuitSolver®, particulate strainer, and isolation ball valves on either side to reduce the number of system components to be installed and minimize potential leak points.
The valve features an integrated O-ring and is factory assembled for a leak-free seal.
How It Works:
The CircuitSolver® Union Assembly with Strainer (CSUAS) balancing valve is installed at the end of each branch in a domestic hot water system (DHWS), downstream of the last fixture, to monitor the water temperature using our exclusive Thermoloid® blend wax actuator technology.
The valve will automatically modulate open or close in response to the changing water temperature to maintain a specified temperature at the end of each branch. This continuous response to temperature variation enables each hot water branch to quickly and consistently direct hot water flow to where it is needed – No manual balancing is required.
The CSUAS will never fully close, allowing a small flow bypass to the return to avoid dead-heading the recirculation pump. The limited flow to your return line will reduce system wear, electricity, and water usage and improve overall system operation.
The CircuitSolver Union Assembly valve with strainer is comprised of a stainless-steel valve, a high-quality O-ring, two isolation ball valves, an integrated strainer, and an optional check valve.
For typical specifications and installation/maintenance instructions, visit the Typical Specs + IMI Steps page.
|1||Valve Body w/ Union Threads||300 series stainless steel|
|2||Union Nut||300 series stainless steel|
|3||Female Threaded Inset||300 series stainless steel|
|4||Plug||300 series stainless steel|
|5||Operating Spring||300 series stainless steel|
|6||Thermal Actuator||300 series stainless steel|
|8||Check Valve (Optional)||Glass Filled Noryl|
|9||Ball Valve, ½” MxF||Brass Lead-Free|
The CircuitSolver® Union Assembly with Strainer is often specified for new domestic hot water systems that may have particulates inside of the system due to construction or in water systems with a history of particulate/dirt issues.
To see CircuitSolver® installations in your area, visit our installations page.
- All Stainless Steel – Corrosion Resistant Construction
- High thrust actuator keeps orifice free of debris
- Union with integrated O-ring for a leak-free seal
- Optional check valve built into the body
- 2 M/F ball valves assembled and leak tested
- Integrated 20 mesh strainer
- Never fully closes, some water always passing through
- Long service life and 3-year warranty
- NSF/ANSI 61 and Zero Lead Content Certified
- Fully compliant with Section 1417(d) of SDWA, the Safe Drinking Water Act
- Supports efforts toward LEED Certification
- Complies with the Buy American Act
- Sizes: 1/2”, 3/4″ & 1”
- Fixed Temperatures:
- 100°F (37.7°C)
- 105°F (40.5°C)
- 110°F (43.3°C)
- 115°F (46.1°C)
- 120°F (48.8°C)
- 125°F (51.6°C)
- 130°F (54.4°C)
- 135°F (57.2°C)
- 140°F (60.0°C)
- Max Working Pressure: 200 PSIG/14 BAR
- Max Working Temperature: 250°F/121°C
CircuitSolver® valves are efficient and take the time typically required to manually balance systems at the end of the project out of the equation. We have started up systems in the afternoon to come in the next morning to find hot water perfectly balanced throughout all risers and zones. Christopher Meurer Plumbing Operations Manager at J.C. Cannistraro, LLC in Boston, MA
By eliminating the conventional method of using fixed flow balancing valves and installing CircuitSolver® valves instead we were able to resolve our lack of hot water in some sectors of the hospital issue instantly. André Renaud Building Consultant at Mental Health University Institute of Quebec
Rittenhouse Hill Apartments - We had a very complicated apartment restoration involving 47 risers. CircuitSolver® saved a lot of time, installed easily, used smaller recirculation pumps to save energy & wear, and continues performing well. Ron Miller President at Adelphia Plumbing in Philadelphia, PA
USC Villages Student Housing - By using CircuitSolver®valves, we saved time and money by not having to balance the system or make any adjustments. It made the process much easier and smoother. Richard Parker Plumbing Contractor at Pan-Pacific Mechanical in Fountain Valley, CA
It usually takes 2-3 plumbers, 2-3 days to balance a system of this size, but by using CircuitSolver® this process was done instantly. Huge savings in terms of time and effort typically devoted to the balancing process. Stephan Thompson Plumbing Contractor at E.M. Duggan Inc. in Canton, MA
CircuitSolver® is a great product. The valves automatically adjust to changing temperatures and pressure drops unlike manual and automatic balancing valves. Plumbing Contractor Production Plus Plumbing in Vista, CA
Before CircuitSolver®, we would have wait times between 5-7 minutes for hot water on the higher floors. Since we have installed CircuitSolver® valves, we are getting hot water when we need it and have not had a single complaint. Robert Schrieber Maintenance Manager at Embassy Suites in Brunswick, GA
The advantages of the system are an efficiently balanced system, saving time testing and balancing the system, lower utility bills and reduced water usage. Luke Holding Project Engineer at The Beck Group in Dallas, TX
I would tell any contractor, building engineer, and mechanical engineer if you are looking at CircuitSolver®, it is simple, it is easy to use, and it works right from the get-go. Chris Watts Plumbing Service Manager at Braconier in Denver, CO
CircuitSolver® makes the initial startup so easy. When we turned it on, the valves balanced the whole system without us having to make any adjustments. We never have any issues when installing them in our projects. Plumbing Contractor Production Plus Plumbing in Vista, CA
We’ve used CircuitSolver®s exclusively now for several years in every application we can. Simply stated, the product is easy to install and works very well with no issues to date. Christopher Meurer Plumbing Operations Manager at J.C. Cannistraro, LLC in Boston, MA
CircuitSolver® was able to automatically balance the system when engineers could not. Mark Wilmink MarkCo Plumbing in Florence, KY
When we install CircuitSolver® valves, it corrects the client’s hot water circulation problems, and everything operates as it’s designed. We are going to keep installing them. Jason Putnam Project Manager at Douglas ORR Plumbing in Miami Springs, FL
The Da Vinci Project - By using CircuitSolver® balancing valves, we were able to save both time and money. The start-up process was much faster by not having to manually adjust each valve. After installation, the system balanced itself and required no maintenance. Arturo Hernandez GJM Engineering in Los Angeles, CA
Right after the installation the general manager went around the building and there was a noticeable difference with quick delivery of hot water. Andy Crossland Principal Mechanical Engineer at Crossland Engineering LLC in Honolulu, HI
What an awesome little device these guys make. It’s a no-brainer. Andy Crossland Principal Mechanical Engineer at Crossland Engineering LLC in Honolulu, HI
I try to have CircuitSolver® specified on as many jobs as possible due to the simplicity of it. Eric McTee Plumbing Designer at ME Engineering in Golden, CO
CircuitSolver®, being that it is an automatic balancing valve, just makes the job of balancing an intricate hot water system that much easier. David Texter Plumbing Engineer at Browne Engineering in Cincinnati, OH
Using CircuitSolver® makes balancing the system so easy. The valves automatically adjust themselves, so you don’t have to check each valve once installed, and there are never any callbacks for issues. Arturo Hernandez GJM Engineering in Los Angeles, CA
It was taking over a minute and a half to get hot water, and now it’s down to 15-20 seconds…also a huge conservation of water…it was a fairly simply retrofit. Robert Albanese Owners Representative for The Austonian in Austin, TX
The University of South Florida - On startup of this install, the system automatically balanced itself in under 3 hours, all without manual labor thanks to CircuitSolver®. The plumbers actually went out a did another job, went to breakfast, and when they came back, the system was balanced. Mike Bishop V.P. of Engineering at RGD Consulting Engineers in Jupiter, FL
Simply stated, CircuitSolver® valves are easy to install and work very well with no issues to date. They’re efficient and take the time typically required to manually balance systems at the end of the project out of the equation. Christopher Meurer Plumbing Operations Manager at J.C. Cannistraro, LLC in Boston, MA
CircuitSolver® makes balancing the system so easy. We don’t have to manually set each line or make any adjustments. We have had absolutely no balancing issues since we started up the system. Richard Parker Plumbing Contractor at Pan-Pacific Mechanical in Fountain Valley, CA
CircuitSolver® is a game changer in balancing DHWS and I would definitely use it as a standard in future projects. Matt Trevino Plumbing Engineer at DBR Engineering in San Antonio, TX
I haven’t come across another product like CircuitSolver®. Once you install the valves you never have to adjust them, unlike manual balancing valves where you have to balance every single valve you install. Richard Parker Plumbing Contractor at Pan-Pacific Mechanical in Fountain Valley, CA